Welcome to the Complementary Multi-Conductor Cable/Phase Calculator
Cable Calculations for Multi-Conductor Cable Runs! Just fill in the required informationdisplayed in the table below!
Multi-Conductor Cable/Phase Calculator
In parallel cables, the phase current is divided between two or more conductors. Typically in paralleling cables, the size and length of each cable are the same, and the current flow is equally divided between the parallel conductors. If the conductors (or lengths) are of unequal size, then the current will not be distributed evenly (i.e. the conductors will carry different currents). Where currents in parallel conductors are unbalanced, it may be necessary to provide separate overload protection for each conductor.
Parallel conductor installations are covered in NEC 310 or CEC 12-108 and are permitted for each phase, polarity, neutral, or grounded conductor in sizes 1/0 AWG and larger. Joining conductors in parallel is like having two or more smaller conductors connected at each end to make one larger conductor.
In order to install conductors in parallel, the paralleled conductors in each phase, polarity, neutral, grounded circuit conductor, equipment grounding conductor, or equipment bonding jumper must comply with all of the following:
The above rules ensure that each set of parallel conductors carries the same ampacity. Where run in separate cables or raceways, the cables or raceways must have the same number of conductors and must have the same “electrical characteristics”.
It is important to use the applicable national codes for your specific installation.
Note: The hashtag (#) symbol on a cell title indicates additional information is available, access it by clicking on the hashtag.
Use your right click button for further help!
|Input Type||Input Unit||Output||Peak Current (#)|
|Derating Factor (#)|
Calculated Cable Size
|Number of Conductors per Phase||Amps per Cable||Cable Size|
Conduit Fill Calculator (NEC)
|Unit||Selection||Max. # Conductors|
|Conduit Type (#)|